Husdata Online (if enabled)
When H60 is installed and all seem to work according to LED statuses and web page, it will start uploading statistics to the Husdata online system every 5 minutes.
Log in to Husdata.se with the by mail supplied account to view real-time information, build reports and configure notification for certain thresholds. It will take 5 minutes before you see the first data.
H60 Web portal
Gives you an overview of your H60 status like its Version, Signal strength, Uptime and statistics.
Heat pump status, parameters and data
A list of the heatpump sensors and status for the heat pump and their current value is shown.
Heat pump settings
In the list there are grey marked rows. These are settings you can change in the heat pump. For example indoor temp and heat curve settings.
NOTE! Settings are not always limited to any boundaries. If you for example only can set the indoor temperature between 10 and 30 degrees using the heat pump display you may be able to set it to 50 degrees in this interface. This will give unpredictable effects on your heat pump operations so please enter values that are valid and verify on heat pump display that they are set properly.
View and make changes to the configuration. See full parameter list in other section of this document.
View about 30 rows of the last messages from the H60 system. The log will reset it self when it gets too large. If first startup log is getting to long it will be stored under the “Startup” log button before cleared. So you can always access the startup information.
Use the ticket function of you like to ask a question or need help. Check the box for Configuration to include it in the ticket. You will get a copy by mail.
The H60 can connect to Husdata support server over an agreed port. This enable Husdata to remotely access the H60 for development or sorting out problems with the unit. To enable Remote Assistance, enter the port number that has been agreed with Husdata as part of the case.
Update H60 firmware
View the current version, releasenotes and new available version of the H60 firware. If they differ you can update your unit by selecting the “UPDATE” button. The update takes about 20-30 sec. Please try to access the unit after 30 sec and verify that it has the new version. Please don’t disconnect the H60 from power while it is updating. After update, please view the Configuration if there are any new parameters that has been added and needs attention.
Update H1 firmware
H1 is the slave-processor of H60 handling heat pump low level communications. If there is an update avalable it will be shown here. Always make sure both the H60, and H1 firmware are updated as they work togehter.
Run console command
For advanced troubleshooting and management, the H60 has a commed console interface when connecting it to its USB/Serial port. Here you can send those console command, however the response will not be seen. See “Advanced” section for more information.
Restart the unit
Restart the H60
Logging out from H60 if password is enabled